Caldera Pirotubular Aquellas donde la transferencia de calor se efectúa por el paso de los gases calientes de la combustión a través de tubos. PARTES PRINCIPALES DE LA CALDERA ACCESORIO DE SEGURIDAD CAMARA DE AGUA Y DE VAPOR MEJORAS La mejora propuesta a. Caldera Pirotubular – Download as PDF File .pdf) or view presentation slides online. Partes de la caldera.
|Published (Last):||24 February 2005|
|PDF File Size:||12.45 Mb|
|ePub File Size:||13.12 Mb|
|Price:||Free* [*Free Regsitration Required]|
For the implementation of the control combustion, is used industrial instrumentation with signal mA as pressure transmitters, flow transmitters, oxygen analyzer, temperature transmitter, and electrical actuators. By Ethernet port is connect the computer for the supervisory of the process by the software of the supervisions and acquisitions of information Vista Plantscape R Once they are removed, the hatches are held in place by revolving hinges that make inspections and any necessary cleaning quick and easy.
These boilers are installed horizontally, with three flues, internal hearth and rear refrigerated hearth chamber. Legal notice and data protection Responsive web developed by Barbitania. Fire-proof materials are not required on the back, resulting in higher performance and lower costs and maintenance.
The principle of the tubular hearth boiler is the oldest and most traditional applied in the construction of steam boilers. Over time, thanks to the technical mastery of cylindrical shapes, improvements have been made to all the possible combinations between heating surfaces and gas piritubular water circulation in order to take the greatest advantage of the heat from fuels.
CALDERA PIROTUBULAR. by Victor San Martin on Prezi
Show simple item record. The front and back of the boiler are fitted with hatches pirootubular access to the flues. The application of any of these depends on different factors, such as: In the automation is used the Hybrid Controller HC Honeywell, this have the ports rs and Ethernet, in the first is connect a flame safety control, this send the information about the ignition of the burner of the boiler.
Uso de cookies Este sitio web utiliza cookies para que usted tenga la mejor experiencia de usuario. They are fastened by screws designed to prevent them from seizing up due to the temperature.
Operacion y Funcionamiento de Caldera Pirotubular.
Combustion occurs and is completed inside the furnace which is completely surrounded and cooled by water. Este sitio web utiliza cookies para que usted tenga la mejor experiencia de usuario.
Some features of this site may not work without pifotubular. Of these, the three-flue version is the one that has spread most worldwide due to both the high performance achieved and to its great versatility, the key to its application in almost all processes where high reliability together with high energy efficiency is required.
The boiler has a manhole at the top and inspection hatches on the front and back to caldrra the inspections and cleaning tasks necessary to keep the inside of the boiler in good condition.
For maximum performance, in the evolution of the design of firetube boilers, gas flues have been added, leading to the development of two, three and even four-flue boilers. The exhaust fumes travel back through the furnace itself before entering the bundle of tubes to make maximum use of the heat and finally being vented into the atmosphere via the smokestack. Contact Us Send Feedback.
Show simple item record dc. Feel free to download technical papers for this product: In the Ecuadorian industrial park the most industries there are not automated this process, many use a mechanical system for control and regulate the air damper modulation and fuel, the main object is free the air and fuel actuator and reduce the fuel consumption of the combustion.