IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||21 August 2012|
|PDF File Size:||7.83 Mb|
|ePub File Size:||9.22 Mb|
|Price:||Free* [*Free Regsitration Required]|
Learn more about the cookies we use and how to change your settings. The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be eic.
The standard is now in your shopping cart. Surge protective devices connected to telecommunications and signalling networks – 60099- requirements and testing methods. It applies to gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in Jec Definitions, principles and rules This part of IEC applies to three-phase a.
Do you need a multi-user copy? SS Valve type surge arresters – Terminology. The methods of analysis are illustrated by practical examples.
Surge arresters – Part 5: Selection and application recommendations
This third edition cancels and replaces the second edition published in This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC This guide gives methods for insulation coordination of different air-insulated systems like transmission lines and substations.
Surge iwc containing both series and parallel gapped structures – Rated 52 kV and less This standard applies to all metal-oxide surge arresters with gaps and housed in either porcelain or polymeric housings. Report error on page. Take the smart route to manage medical device compliance.
Part 5 Selection and application recommendations This standard provides recommendations for the selection and application of surge arresters to be used in three-phase systems with nominal voltages above 1kV. Your shopping cart is empty.
This guide recognizes that a perfect line design does not exist, and that a series of compromises are made in any distribution-line design. This new edition covers new mechanical test requirements for polymer and porcelain housed arresters.
Selection and application recommendations.
Preview Insulation co-ordination – Part 2: This standard also specifies requirements and tests for metal-oxide surge arresters with internal series gaps, with rated voltages of 52KV and below Preview Surge arresters – Part 7: It also gives the lists of the standard withstand voltages from which the rated withstand voltages should be selected. This standard recommends that the selected withstand voltages should be associated with the highest voltage for equipment.
More complex and special solutions requiring study by experienced engineers is described, but specific solutions are not always given. Copyright – ArresterWorks. Click to learn more. Related publications IEC It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters.
In many cases, the prescribed steps are adequate. The procedures are based on theoretical studies, test results, and experience.
We accept all major credit cards American Express, Mastercard and VisaPayPal and bank transfers as form of payment. This association is for insulation co-ordination purposes only. An additional section discusses several special methods that 6099-5 be used to improve lightning performance.
The protective equipment is mentioned in clauses 1.
BS EN – Surge arresters. Selection and application recommendations
Systematic directions toward proper solutions of various applications are provided. The designer may exercise control over structure material and 600099-5, shielding if anyamount of insulation, grounding, and placement of arresters.
You may find similar items within these categories by selecting from the choices below:. Metal-oxide surge arresters without gaps for a. Non-linear resistor type gapped surge arresters for a.